Sodium Hypochlorite Sterilisation Recirculated (SHSR)
MAK Water’s Sodium Hypochlorite Sterilisation Recirculated (SHSR) are designed to automatically maintain the correct amount of free chlorine in a potable water storage tank, in accordance with Australian Drinking Water Guidelines (ADWG). The standard treatment process includes a recirculation pump to turn over the contents of the potable water storage tank twice in a 24 hour period, an inline chlorine analyser which monitors residual free chlorine and a dosing pump to automatically dose liquid sodium hypochlorite as required
The system components are sized to suit the potable water storage tank and daily water usage. Options are provided for duty standby recirculation and dosing pumps to improve plant reliability. MAK Sodium Hypochlorite Sterilisation Recuirculated plants are available skid mounted for installation inside a building, or containerised with air conditioning to avoid chlorine degradation.
Disclaimer: MAK Water is continuously updating and improving its products and services, so please contact us for more detailed information or to confirm speci - fications. MAK Water takes no responsibility for any errors resulting from the use of information contained within this document.